Freight deliveries require a delivery time be scheduled and someone must be present at the time of delivery to inspect and sign for the merchandise. A representative from the freight carrier will call the phone number entered at checkout to schedule the delivery.
Freight orders placed before 3PM EST (M-F) ship same day.
For freight deliveries, you have the option of adding a liftgate to your delivery. A liftgate is the device that lowers a product from the truck to ground level.
CPO recommends adding liftgate service for freight deliveries exceeding 100 lbs if you do not have a loading dock or fork lift at the delivery address. Additional charges may apply. The liftgate option will be presented during the checkout process.
Please note that liftgate service only ensures the product is removed from the truck. We recommend you have the additional help of two to four people to move the product to its desired location because drivers are not required to assist.
Requesting liftgate service after ordering may result in additional charges and delays.
|Amperage - LP Vapor:||41.7|
|Amperage - Natural Gas:||37.5|
|Engine Displacement:||803 cc|
|Fuel Consumption - LP Vapor:||1.13 Gallons at 50% / 1.887 Gallons at 100%|
|Fuel Consumption - Natural Gas:||76.5 cubic ft at 50% / 131.5 cubic ft at 100%|
|Fuel Type:||Propane (LP Vapor) / Natural Gas|
|Rated Watts:||10 kW|
|Rated Watts Output - LP Vapor:||10kW|
|Rated Watts Output - Natural Gas:||9kW|
|Transfer Switch:||Sold Separately|
|Transfer Switch Amperage:||100 - 200 Amps|
|Transfer Switch Required:||Briggs and Stratton Models 71045, 71046, 71047|
Do you have questions about this product?
get answers from real customers and in-house experts with AnswerBox.
Q:with the standby home generator system. Can I connect this system to my homes electrical system and utilize my existing electrical box and circuit breakers? Or do I need the 100 amp, 16 circuit breaker box you sell as an accessory?
A:That would depend on the rating of your existing panel. This generator requires a transfer switch which is sold separately and the rating on that is 100 - 200 amps. In that instance you would feed your transfer switch from the utility and then feed your existing panel from the transfer switch.